Target Storage is glad to announce receiving the Letter of Acceptance (based on our new design layout proposal) from Fire Services Department for the latest fire safety guidelines of mini storage.
Mainly the following points have been noted and/or being improved within our facility:
1) Minimum 6.25% window area based on total floor area. (Minimum 2% emergency access widows easily accessible, with minimum 1m x 0.85m size access window size, and with maximum window starting height of 1.1m measured from floor to bottom of window).
2) Maximum 50 sq.m of net customer storage area for each new cubicle zone.
3) Each corridor of storage zone should not exceed 20m length distance.
4) Maximum storage height of 2.35m, with 1m empty space required measured from maximum customer storage height to concrete ceiling.
There are more general safety guidelies from FSD (Fire Service Department) to list, but the above are the most important ones which we are currently upgrading and modifying to compliance based on the latest regulation for all mini storage operators in Hong Kong.
We much appreciate all our current customers for their kind understanding to these new safety regulations.